During a normally scheduled monthly generator test, one of the UPS
created a short power fluctuation during the power switching over.
We are working with the equipment manufacturer to determine the cause of
this issue. A few pieces of our network hardware were affected and causes us to have to restart and test some server hardware which took some time.
We do generator tests every month and this is the first issue we have experienced with it.